The Causes of Concrete Deterioration
Reinforced concrete can be a highly durable structural material requiring little or no maintenance. However, it is now recognised that without correct design, mixing, placement and curing, the durability of reinforced concrete may be impaired. Further protection should be provided immediately after construction if durability is to be achieved. Steel reinforcement in well-designed concrete structures is protected from corrosion by the passivating effect of the highly alkaline concrete cover. Concrete decay can arise from the failure of the “passivating effect”.
Neutralisation of the alkaline layer around the steel by the reaction with carbon dioxide causes carbonation of the concrete cover and results in loss of alkalinity. Loss of alkalinity at the interface between concrete and reinforcement is generally associated with:
Inadequate curing of the concrete. Poor compaction of the concrete. Permeable cover allows the penetration of carbon dioxide which reacts with the free lime to produce mildly acidic carbonates.
Chlorides attack the reinforcing steel through electrolytic action producing black coloured rust. In dense high strength concrete, a significant loss of the reinforcing bar can take place without the normal visible signs of disruption to the concrete cover, such as spalling.
Alkali Silica Reaction (ASR)
Cracking may be caused by the formation of an expansive gel through the reaction of alkali with reactive silica, usually caused by high levels of alkalis in permanently wet concrete.
High Alumina Cement (HAC) Conversion
Concrete containing high alumina cement with high water-cement ratio will often suffer conversion, a progressive degradation of the hardened cement paste.
In both HAC conversion and alkali silica reaction, there is no known cure or treatment. Any patch repairs and external protective treatment can only delay the inevitable decay.
In Facades where the concrete specification is often lower than for highway structures, the chance of the concrete being permeable is greater and so more prone to carbonation. Chlorides may also be a problem in areas of atmospheric pollution or where calcium chloride was used as an accelerator.
In Infrastructure, such as highways, the concrete specification is more rigorous resulting in dense impermeable concrete, resistant to carbonation Highway structures suffer mainly from the penetration of chloride ions from applied de-icing salts
In establishing the causes of failure, concrete repair contractors will test for both carbonation and chlorides. When chlorides are present, preparation for the remedial concrete repair needs greater attention i.e. cleaning and protecting the steel. The future protection of the structure may also need to be different. For reinforced concrete suffering from both carbonation and chloride attack, it is necessary to follow the procedures for dealing with chloride decay.
Testing for carbonation is relatively simple -a freshly broken out piece of the concrete sprayed with phenolphthalein solution remains grey where carbonation has taken place but turns pink if still highly alkaline. Detecting for levels of chlorides will require laboratory analysis, but on-site test kits to show the presence of chlorides is available. The depth of cover can be measured using a properly calibrated cover meter.
Construction of Deck level pool shell
Mr RW Cargill
Construction of 20M swimming pool
Construction of pool shell
"Delighted by Contech UK's workforce performance. Staff were punctual, understanding, consistent and proactive. Overall a very professional experience."
Exeter School Competition Swimming Pool
Completed project: swimming pool and hydro pool shuttering, reinforcement, spray concrete.
Nigel Busby, Project Manager at ISG, said he was very happy with the standard of our work, our on-site team were very helpful and the finished concrete dimensions were spot on.
"Great end product which was brought in on programme. A pleasure and a breath of fresh air to deal with."
Swimming Pool Shell installation
After we completed sprayed concrete to contiguous piles for a two-storey basement car park in Bournemouth: "Works were completed on schedule to a high standard. A very professional service".
Completed project: spray concrete along the River Hull estuary.
Matt Malik, Package Manager for C Spencer Pioneer Engineering said that Contech UK carried out a professional service with a can do attitude. All workmanship was signed off with a defect free handover.
Completed project: Swimming pool shell construction.
John Holder, Senior Project Manager at ISG said that our works were undertaken to a good, overall, standard.
Senior Project Manager
If you have a particular project you would like further information, advice or a quotation for then please provide us the details by filling our project enquiry form.Click here now
Registered office: Unit 1 & 2 Hereford Road, Pocklington Industrial Estate, York, YO42 1NR...
© 2021 All Rights Reserved